All OMRON products are capitalized in this manual. The word .. purpose and a comparison between the CQM1H and the CQM1. Section 2. 1. V4+. Voltage pin, input 4. 2. V Common pin, input 4. 3. V3+. Voltage pin, input 3. 4. V Common pin, input 3. 5. V2+. Voltage pin, input 2. 6. V Common . View and Download Omron CQM1 operation manual online. Programmable Controllers. CQM1 Controller pdf manual download. Also for: Sysmac cqm1.
|Published (Last):||7 January 2017|
|PDF File Size:||4.77 Mb|
|ePub File Size:||5.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
Read the integral time. In some environments, the shielded wire of the two-conductor twisted-pair cable should be connected to the COM terminal instead of the FG terminal of the Analog Input Unit so that the Analog Input Unit will not be influenced by external noise. Applicable Connectors Use the following products or equivalents for the connector on the cable side. Nomenclature And Settings Nomenclature Not lit when set to 16IN. Connector Type Dimensions when Mounted mm Approx.
Section Commands and Responses Response If the output word is set to the correct command code, the sign of the scaling value and the scaling value will be set to the input word alternately in the fol- lowing format.
Input the final operand and then press the WRT Key. See indirect address and DM area. Bring up the initial display. Revision History Page Slide the module selector and set to 1 for module 1, 2 for module 2, and 3 for module 3.
Page 11 Conformance to EC Directives When switching a load with a high inrush current, such as an incandescent lamp, suppress the inrush current as shown below. Please read this manual carefully and be sure you understand the information provide before attempting to install and operate the CQM1.
Omron CQM1 Operation Manual
Not lit when set to HOLD. CPU Unit Section removed will not be fully charged and memory may be lost before the new battery is inserted. Place the object at the sensing position at which the desired output will be OFF and press the teaching button. Page OFF if this error occurs. All dimensions are in millimeters. The input word has flags for comparison results, overrange detection, and sensor disconnection detection as shown below. The heater burnout alarm output will turn OFF if the setting is changed to 0.
Word n Data output An operation control command must be executed to start actual opera- tion. Vibration resistance 10 to Hz, 0. This operation checks for programming errors and displays the program address and error when errors are found. Perform positioning teaching within the stable sensing range.
OMRON CQM1 OPERATION MANUAL Pdf Download.
Nomenclature And Functions Remote Console If the input type data is changed, the scaling value will be set to the factory-set scaling value. Countermeasure 1 Countermeasure 2 Providing a dark current of approx. This indicator cannot be used to detect the disconnection of 9. M3 optimum tightening torque: Terminals B and B also short-circuited internally. It is possible in any mode. Bit 15 of the input address is allocated as follows, according to the DIP switch input mode setting.
Page 57 Not lit when there is an error in the Expansion Master. Example If the user wants to write derivative time to the output word and a control period to the input word, input C as the allocation change code to be writ- ten.
You must read this section and understand the information contained before attempting to set up or operate a PC system. The command codes can be set to output word. The Appendix provides kanual specifications for the Unit. While CC00 is set to the output word, the A or A00F and the present scaled conversion data will be repeatedly displayed alternately at approxi- mately 0.
Page 70 28 Slaves G Remote Terminals. Switching Capacity 50 mA at 4. Press the CHG Key to begin decimal data modification. Although single-unit Programmable Controllers are available, building-block Programmable Controllers are constructed from separate components.
Nomenclature Ready indicator green, lit when the Unit is rec- Word number indicator orange, lit when two words are ognized as the Temperature Control Unit used and not lit when a single word is used Terminal screws: Monitoring The input word has flags for comparison results, overrange detection, and sensor disconnection detection as shown below.
Xqm1 during stable light ON or dark ON, which can be selected with the operation mode selector.
An automatic teaching function is Separate Amplifier incorporated.