This calculation is based on IEC (, c), “Short-circuit currents in three-phase a.c. systems – Part 0: Calculation of currents” and. EasyPower offers a complete and accurate solution to short-circuit calculations in three-phase AC systems using the IEC standard. You can enter. IEC Edition INTERNATIONAL. STANDARD. NORME. INTERNATIONALE. Short-circuit currents in three-phase a.c. systems –.
|Published (Last):||7 April 2017|
|PDF File Size:||11.48 Mb|
|ePub File Size:||11.73 Mb|
|Price:||Free* [*Free Regsitration Required]|
This postulates that the electrical equipment has a balanced structure, for example in the case of transposed overhead lines. In this case, the symmetrical short- circuit breaking current Ib is smaller than the initial symmetrical short-circuit current I,”. The values of positive-sequence and negative-sequence impedances can differ from each other only in the case of rotating machines.
The value should be obtained from the manufacturer. Sequential short circuits are not considered. For minimum short-circuit currents, the resistances are based on the estimated temperature at the end of the short-circuit condition. For the short-circuit impedances of synchronous generators in the negative-sequence system, the following applies with KG from equation 1 8: In this case special considerations beyond the scope and procedure given in this standard have to be taken into account see for instance 2.
This part of IEC establishes a general, practicable and concise procedure leading to results, which are generally of acceptable accuracy.
IEC Short-Circuit in EasyPower
Transformers in Parallel The following features are supported: Figure 21 – Factor m for the heat effect of the d. For phase currents, the maximum current of the three phases is used.
Symmetrical Short-Circuit Breaking Currents I b For rotating machines the current 60990 to short-circuit decays over time. You can modify these values as needed in the short circuit options. All other active voltages in the system are assumed to be zero.
Phasor diagram of a synchronous generator at rated conditions For a synchronous generator use Rm see 3. In meshed networks there are several direct-current time constants.
609099 equations 46 and 47 are given for the calculation of and in figure 3c: EasyPower provides the option of showing a warning when the short-circuit duty percent is above a user defined safety margin threshold but below iwc violation level. I k autre s Low-voltage motors are to be taken into account in auxiliaries of power stations and in industrial and similar installations, for example in networks of chemical and steel industries and pump- stations. By understanding the theory any software allows users to perform all the necessary calculations with ease so they can work on the design and application of low- and high-voltage power systems.
You are currently using the site but have requested a page in the site.
Short Circuits in Power Systems: A Practical Guide to IEC 60909-0, 2nd Edition
For undated references, the latest edition of the normative document referred to applies. The method described above is for 3-phase short iex. IEC section 6 provides a sample calculation as a benchmark test for software programs to compare.
The effective resistance of the stator of synchronous machines lies generally much below the given values for RGf. Earth ground trip functions for low voltage circuit breakers or relays use the symmetrical earth ground current. Ik Steady-state short-circuit current r. Time-current characteristic curves showing device curves clipped at the right side and short-circuit tick marks.
Design and Calculation of aWind Farm 8.
Synchronous Generator Impedance Correction Factor The synchronous generator impedance correction factor K G for generators without unit transformers is calculated as follows per section 3.
The total short-circuit in F1 or F2 figure 13 is found by adding the partial short-circuit current ILrnv, caused by the medium- and low-voltage auxiliary motors 06909 the power station unit.
IEC | IEC Webstore
Short-circuit on any bus results in voltage drop in other near buses in the system. For TCC clipping you can choose one from initial, breaking and steady state currents.
Figure 1 – Short-circuit current of a far-from-generator short circuit with constant a. International, governmental and non-governmental organizations liaising with the IEC also participate in this preparation. Thus the network feeder in figure 4a is represented by its internal impedance Zot, transferred to the LV-side of the transformer see 3. Asymmetrical values can be used with protective devices that respond to the asymmetrical currents.
U, is the nominal voltage of the system; ur, is the rated voltage of the generator; ZGK is the corrected subtransient impedance of the generator; 2, is the subtransient impedance of the generator in the positive-sequence system: Impedances between a starpoint and earth shall be introduced without correction factor.
NOTE For some near-to-generator short circuits the value of id.
The short-circuit impedances for 6009 equipment are modified using impedance corrections factors that are calculated based on section 3. For balanced and unbalanced short circuits as shown in figure 3, it is useful to calculate the short-circuit currents by application of symmetrical ie see 2.
Figure 3 – Characterization of short circuits and their currents Figure 4 shows an example of the equivalent voltage source at the short-circuit location F as the only active voltage of the system fed by a transformer without or with on-load tap-changer.
Iev a number of short circuits occur with a short time interval in between them, the resulting Joule integral is the sum of the Joule integrals of the individual short-circuit currents, as given in equation 1 IkP Steady-state short-circuit current at the terminals poles of a generator with compound excitation Initial symmetrical short-circuit current r.
IEC-60909 Short-Circuit in EasyPower
In general, the calculation according to 4. EasyPower calculates the Peak currents i p based on section 4. Added to Your Shopping Cart. This figure is useful for information but should not be used instead of I calculation.
NOTE The current in a three-phase short circuit is assumed to be made simultaneously in all poles. Definitions,principles and rules IEC 1: